From: £240.00 ex VAT
Recessed ceiling heaters are designed for installation into either a standard suspended grid or plasterboard ceiling, wherever there is sufficient space above to accommodate them. They can be installed as the main or supplementary heating in shops, reception areas and offices. Locating the units in positions of greatest heat loss gives an easy solution to uneven heating of open plan areas.
Tucked away in the ceiling space of a standard suspended grid or plasterboard ceiling, this electric fan heater is ideal for use where available wall and floor space is limited or where a clean or minimal interior design style is applied. With a fan driving the warm air downwards it helps to counteract cool air creeping in from drafts and hovering at lower levels . Even in fan only mode (non-TT versions), it acts as a de-stratification device balancing the air temperature from floor to ceiling ensuring a comfortable temperature at floor level.
The minimal height of the unit allows it to be fitted within a ceiling void of 250mm. The maximum recommended mounting height is 3m.
Connection should be made to a suitably fused power supply via the remote switch unit or a 2 pole switched connection unit having a contact separation of at least 3mm in all poles. Access to the connector block is gained by opening the side cover plate (1 screw), connection is then made using cables with 4 cores and earth, with at least one being rated to take the full load current.
All electrical connections should be made by a suitably qualified person in accordance with the latest edition of the IEE Requirements for Electrical Installation (BS 7671:2008).